China professinal manufacture YCM1 mccb 160a
1.1 Electric ratings:AC 690V,50/60Hz,10~800A;
1.2 Mounting mode: vertical and horizontal;
2.1 YC:company code
2.3 1:design sequencenumber
2.4 :frame size
2.5 :code of breaking capacity:L/M/H
2.6 :operation mode
2.7 :number of poles
2.8 :release type and accessory code
2.10 :type of N-pole for 4-P breaker
-5°C~+40°C; the average value within 24h shall not exceed +35°C.For the circuit breaker with thermo-magnetic release,+40°C is set to be the standard temperature for rating.For temperature not between -5°C~+40°C,please contact us for temperature compensation correction:
Not exceed 2000m(Please contact with us for reduction coefficient if altitude at the mounted site exceed 2000m)
3.3 Air conditions:
At mounting site,relative humidity not exceed 50% at the max temperature of +40°C,higher relative humidity is allowable under lower temperature.For example,RH could be 90% at +20°C,special measures should be taken to occurrence of dews.
|Type YCM1-63 YCM1-100 YCM1-225 YCM1-400 YCM1-630 YCM1-800|
|Poles||P|| 3||4 3||4 3||43||43||43||4|
|Rated current in||A|
10,16,20,25 10,16,20,25, 100,125, 200,250, 400,50
32,40,50,63 32,40,50,63, 160,180, 315,350, 0,630
80,100 200,225 400
|Rated insulation voltage||V||690 800|
|Rated impulse withstand voltage Uimp||V||6000 8000|
|Rated operation voltage Ue||V||400 AC400/690|
|Breaking capacity class||L||M L||M||H||L||M||H|
1.China top 500 enterprises.
2.26 years rich experiences in manufacturing electrical products.
3.Sales in over 100 countries.
4.Pass ISO9001,ISO14001,CCC,CE,CB,IEC,ICO certificate and standard.